Water Well Tanks
Ask Us About Our Well Chlorination Kits.
Quality Water Well Tanks Repair & Installation,
Peter Snelten & Sons
Family-Owned & Operated Since 1923.
Serving Cook County, McHenry County, Lake County,
Kane County & Dupage County Illinois.
When It Comes To Water Well Service & Installations Peter Snelten & Sons Takes Every Job Seriously, We Provide The Most Economical & Practical Solutions In The Water Well Industry Available Today.
When sizing a pressure tank for your system, you first have to look at what the pumping capacity is. Pressure tanks are designed to hold 1/3 water and 2/3 air. The pressure tank should be large enough to allow the submersible pump to run for, at least one minute. This allows the cold water passing by the electrical motor to actually cool it down. When submersible pumps and pressure tanks are properly sized for your water well system based on how many faucets you have in your home, they will provide years of reliable service. Remember, a submersible pump a little too large will always do the job properly, and a submersible pump that is sized a little too small will have to be replaced or will prove unsatisfactory for your needs.
Well-X-Trol is the standard of the industry with many unique features including high strength steel to deliver 150 PSIG working pressure, a patented Turbulator water circulator device, and a patent-pending antimicrobial liner that neutralizes bacteria on contact. Well-X-Trol product features innovative design that uses a hoop ring and groove to lock the diaphragm, liner, and shell together.
Well-X-Trol is the world’s most trusted brand of well tanks, backed by an industry-leading 7-year limited warranty.
Highest Working Pressure – 150 PSIG.
Strongest Tank Design Featuring Deep Drawn Steel and Multi-Dome Construction.
Thickest Diaphragm – Heavy-Duty Butyl.
Toughest Indoor/Outdoor Coating – Tuf-Kote™ HG.
Longest Warranty – 7-Years.
Patented Turbulator™ Water Circulation Device.
Patent Pending Antimicrobial Liner to Neutralize Bacteria on Contact.
Stainless Steel System Connection.
Welded Air Stem to Help Eliminate Leaks.
Patented DuraBase® Composite Stand Never Corrodes.
Optional Pro-Access® Connection for Faster Installation.
Shell: High Strength Steel
Diaphragm: Heavy Duty Butyl
System Connection: 304L Stainless Steel
Stand: Steel or Patented DuraBase®
Finish: Tuf-Kote™ HG Blue, Tan or Gray
Water Circulator: Patented Turbulator™
Air Valve: Projection Welded
Factory Precharge: 38 PSIG (2.6 bar)
Max. Operating Temperature: 200º F (93º C)
Max. Working Pressure: 150 PSIG (10.3 bar)
Max. Relief Valve Setting: 125 PSIG (8.6 bar)
Warranty: 7-Year Limited
Controls pump cycling in residential water systems.
Can be used indoors or outdoors.
The optional, patented DuraBase stand is rugged; never corrodes.
They were absolutely excellent. We called them, and they showed up as soon as they heard from us. They fixed our problem in half a day. Our well was completely shot and we had no water in our house. After their repair, our water works even better than before. We’re so thankful for them. WE LOVE THEM!!
~ Steven Singh
I called and they came out within 30 minutes! Very nice and informative. Overall great experience! Will definitely recommend them.
~ Christopher Kersten
We lost power and my water did not come back on. I thought for sure it was the well pump. Kyle came and tracked the problem down. I put the wrong kind of switch on the pressure tank. Save me a bundle, very pleasant. Highly recommend.
~ Ron Bachman
Family oriented. That’s important to us. Thank you for helping out immediately when we had a big problem. We highly recommend this company.
~ Dorothy Euchler
Our water was not working this morning and I called our local guy and he no longer is in service. So I found these guys on the Internet wanted to pass along the information. I called them at 7:30 this morning and they were here by nine. They moved their schedule around so they could get here sooner because I did not have water. If you need well service give these guys a call they were great!
~ Kimberly Kearney
Yesterday, at 1:00 we called Snelten and Sons about getting a switch repaired and they were at our house at 2:30. Ben and Adam were very courteous, professional, and informative. They did not take any shortcuts, they did the job efficiently and the price was fair. Highly recommend this company to anyone who has well water.
~ Daniel Pfligler
Todd Snelten did a wonderful job working on my well and water pressure tank. I highly recommend them for your well and water needs. They were here in 90 minutes after my phone call and replaced everything but a new well and was completed the same day they started the work.
~ Joseph Doyle
Every time I have service done from this company it is 100% top notch! Thank you for all the GREAT service you have provided to us for the last 32 yrs!!
~ Michael Glefke
~ Kristi Weseman
~ Terrie Warzecha
~ Robert Ross
~ Melissa J.
~ Michael J.
Mon – Friday 8-5
Luke – 224-656-4912
Thank You For Considering Us For Your Well Drilling & Service & Repair Needs
Water Well Drilling
Complete Water Well System Installations
Submersible Pump Repair & Replacement
Shallow Well Pump Repair & Replacement
Pressure Tank Replacement
Peter Snelten & Sons
25000 S. Old Rand Road
Wauconda, Illinois 60084
Cook County, IL
Lake County, IL
McHenry County, IL
Kane County, IL
DuPage County, IL